How to conduct a fire door safety check
If you’ve read our previous blog post on the new legislation surrounding fire doors in buildings above and below 11m, your next question might be how to conduct a thorough fire door safety check
As part of their Fire Door Safety Week campaign, the British Woodworking Federation (BWF) set out a simple 5-step fire door check. Check out the key points below:
Find the certification label or plug. These are usually sited on top of the door, however they can occasionally be found on the side. If no label can be found, this may not be a certified fire door and should be reported.
Top tip: using a mirror or the front facing camera on your phone makes this easier!
The gaps around the top and sides of a fire door must be consistently between 2-4mm when the door is closed, with a gap tolerance of up to 8mm underneath the door. Excessive gaps mean that fire and smoke may be able to travel through and should be reported.
Top tip: a £1 coin is around 3mm thick and so can be used to help you get an idea for scale.
Look around the door or frame to identify any intumescent seals, checking that they are intact with no signs of damage. Any damage to these seals may prevent them from expanding in heat as designed which will hinder their ability to stop the passage of fire and should be reported.
Open the door and check that all hinges are firmly fixed. There should be at least three hinges per door with no missing or broken screws. Hinges which are not securely attached mean that the door may not be able to withstand the intensity of a fire as it should and should be reported.
Top tip: hinges which are not securely attached could also indicate that a door has not been well maintained
- Closing Properly
Ensure that the door closes firmly onto the latch without sticking on the floor or frame. You can do this by opening the door to around halfway, then letting go to see what happens when you allow it to close by itself. A fire door which is not able to fully close by itself will not be able to perform as it should in the event of a fire and should be reported.
Top tip: fire doors are only able to perform when closed and so should never be wedged open.
FrameFit offers a unique retrofit system which can be applied to doors with excessive gaps between the leaf and frame, quickly and easily bringing existing fire doors back into compliance.
By becoming part of the old system, FrameFit saves time, money and resources, whilst aiding in budget management over time.
For more information about FrameFit, contact our friendly team of experts today!
T: (0) 1442-899-942